Microsoft KB Archive/89465

= LAN Man 2.1 Test Summary (American Power Smart-UPS 2000) =

Article ID: 89465

Article Last Modified on 10/31/2006



This article was previously published under Q89465



SUMMARY
The following are the test results for the Smart-UPS 2000 uninterruptable power supply (UPS). The test was conducted as part of the Microsoft Compatibility Lab (MCL) peripheral test for LAN Manager version 2.1:



Manufacturer
American Power Conversion

132 Fairgrounds Rd.

West Kingston RI 02892

(800) 800-4272

Date Tested
5/26/92

Uninterruptable Power Supply Data
Model:                         Smart-UPS 2000 Serial number:                 W205222745 Supplied cable part number:    940-0020A Vendor supplied software:      N/A Software part number:          N/A

UPS Switch Settings
Switch Number      Setting -      ---     1               OFF 2              OFF 3              OFF 4              OFF The switch settings used are also factory defaults.

Testing Environment
Operating system:     OS/2 1.3 Network:              LAN Manager 2.1 Test platforms:       486/33 16 MB RAM Bus specification:    EISA Network topology:     Ethernet

LANMAN.INI [UPS] Settings
BatteryTime:         60 CmdFile:            N/A MessDelay:            2 MessTime:           300 Recharge:           100 Signals:            111 VoltLevels:         111

Final Test Results
Test Focus                          Pass   Anomalies and/or Workarounds --                             Installation                          Yes Fully chargeable                     Yes Power lost signal                    Yes Power restored signal                Yes Low battery signal to server         Yes Shut down server                     Yes Server boots when power restored     Yes Sustains server power for 5 minutes  Yes

Additional query words: certification 2.1 2.10

Keywords: KB89465

-

[mailto:TECHNET@MICROSOFT.COM Send feedback to Microsoft]

© Microsoft Corporation. All rights reserved.